Cadet Manufacturing Com-Pak Bath Heater CBC103TW
You Are Here: Home
> Cadet Manufacturing Heaters and Parts
> Cadet Manufacturing Heaters
Cadet Manufacturing Com-Pak Bath Heater 65101 CBC103TW
We are the Factory Authorized Master Parts Distributor for Cadet Manufacturing. Call us today for all of your Cadet Manufacturing heater, parts and accessories needs. Toll Free: 1-877-733-9241
Features and Benefits
Ideal for instant warmth in bathrooms
- High temperature manual reset:
Turns off heater if normal operating temperatures are exceeded
Durable steel tube and plate constructed heating element - painted to resist rusting
Advanced built-in controls
- Thermostat: range 45º-85ºF with disabled (no heat) position
- 60 minute timer overrides thermostat for instant warmth
Powder coat paint process eliminates sharp metal edges
Multi-Volt and Multi-Watt options
Unique low profile grill only 1/2” deep
Fan forced electric air heaters shall be UL listed, factory rated at 120V/240V or dual field rated from 208V to 240V. The painted wall mounting can is made from 20-gauge sheet metal with six electrical knockouts and a 22 cubic inch wiring compartment. Each heating unit shall be of unitized construction and attach to the wall can with a single screw and shall be self contained and completely separate from the wall mounting can. Elements shall be tube and plate, painted, with an over-sized 16 amp rating at 240V high temperature manual reset limit switch. A centrifugal blower shall be driven by an impedance protected motor. The motor shall be totally isolated from the heating element. Metal grill shall be of one piece, 20-gauge construction, and finished with a powder coat paint system.
All heaters include a built-in single pole thermostat and 60-minute timer. The Com-Pak Bath Heater is not to be used with a wall thermostat. The multi-volt option must be configured for the correct voltage before installing the heater. The multi-watt option must be configured for the desired wattage before installing the heater. UL requires heater to be placed a minimum distance of 6” from adjacent surfaces and 4.5” from the floor. Manufacturer recommends installation 12” from all surfaces. A 3’ minimum clearance is required for furniture or other objects placed directly in front of heater.
NOTE: Manufacturer recommends installing heater assembly after walls are finished. Heater must be cleaned every six months minimum.
Rough In Dimensions: 8"W x 10.25"H x 4"D
Wall Can Dimensions: 7.875"W x 11.5"H x 4"D
Grill Dimensions: 10"W x 12.625"H x .5"D
The 65101 Cadet Manufacturing Com-Pak Bath Heater CBC103TW is a stocked item and ready to be shipped to you today.
Click on a state to
check in-store availability:
Stock levels are updated once a day and can change without notice.
> Help Finding Your Model #